San Francisco Code Compliance
The San Francisco Remote Fill features the common leak detector alarm and the two dry contact alarm monitors required by the Fire Department. The machine operator must place the fill switch activated for a fill operation in the on location. In the regular or bottom tank, the control panel controls the level. The solenoid valve opens when fuel hits the high level and the warning light is triggered in the remote fill and at the control panel. A system operator is allowed to silence the alarm local from the remote fill or control pane, but until the fill switch is placed out, the alarm light remains illuminated and energized. The control panel monitors the remote filling and top of the day or belly tank leak detectors. The control panel for a piping tray or piping sump provides an input of the replacement leak detector.
The remote supply system consists of a remote filling box NEMA 4 and a remote fill control panel matching NEMA 4. A flush or fixed surface or free standing with an optional rack may be the mobile fill enclosure. The unit is fitted with a full warning, whistle, silence and fill toggle. Quantity Description, You’ll receive 1 Remote fill control panel, 1 Remote Fill Enclosure with integral light and horn, which silences and fill enable switches, 1 High level float switch, 2 Leak detectors and 1 Normally open solenoid valve.
Parts number: • Dry detach and cover, remote filling panels with silence switch, lamp, horn and warning lighting system, remote control panel, single filling panels, shipped unloose, level check tank, shipped loose, two leak detectors, shipped loose, and one inch, Usually opening solenoid valve, shipped loose. Shipped unloose.
- Dimensions: 24 X 24 X 24
- Flush mount unit has 2 inch flange on all sides.
- Weight: 85 lbs
- Construction: Welded steel construction of enclosure. The unit
includes a kamvalok fitting and dust cover. The unit does not include any piping. Piping may enter on the top, bottom, back or sides.
- Controls: Ships with matching remote fill control panel.
- UL Listing: UL 508
- Capacity: Secondary containment is 5.3 gallons.
- Power Required: 120 volts, dedicated circuit at control panel. Remote fill enclosure light and horn are powered from matching control panel.